18.104.22.168 Grease filters shall be listed and constructed of steel or listed equivalent material
22.214.171.124 Grease filters shall be rigid construction that will not distort or crush under normal operation, handling, and cleaning conditions.
126.96.36.199 Grease filters shall be arranged so that all exhaust air passes through the grease filters.
7.3.1 Openings shall be provided at the sides or at the top of the duct, whichever is more accessible, and at changes of direction.
188.8.131.52 If not easily accessible from a 3 m (10 ft) stepladder, opening on horizontal grease duct systems shall be provided with safe access and a work platform.
184.108.40.206 Approved upblast fans with motors surrounded by the airstream shall be hinged, supplied with flexible weatherproof electrical cable and service hold-open retainers, and listed for this use.
220.127.116.11.1 Upblast fans shall be supplied with an access opening of a minimum 76 mm by 127 mm (3 in. by 5 in.) or a circular diameter of 101 mm (4 in.) on the curvature of the outer fan housing to allow for cleaning and inspection of the fan blades.
11.6.10 When an access panel is removed, a service company label or tag preprinted with the name of the company and giving the date of inspection or cleaning shall be affixed near the affected access panels.
Facilitec Southwest is the leading provider of Restaurant Kitchen Exhaust Cleaning Services and Rooftop Grease Containment products in the Southwest United States. Our satisfied customers include chain and independent restaurants, hotels, casinos, hospitals, supermarkets, country clubs, schools, cafeterias, food processing and industrial organizations. Give us a call and let us show you what we can do for your establishment. We are fully insured and bonded.
If your question has not been answered, please Contact Us. and we would be happy to help you.
2300 Cold Springs Road
Fort Worth, TX 76106
Toll Free: 1-866-466-3339